Things You'll Need
Duct crimping tool
1/2-inch-long self-tapping sheet-metal screws
Cordless drill or screwdriver with proper bit to drive screws
Foil tape for HVAC applications
2 flat-head screwdrivers
Raw edges on duct work are extremely sharp, so use caution when handling all sheet metal.
Residential duct work supplies heated or cooled air to the living space from the furnace and returns the same amount of air from the living space back to the furnace. This process provides a mixing of the air and maintains proper air pressure in the house, especially when the windows and doors are closed. The duct work is made of pieces of sheet metal that are either round or rectangular. These pieces are connected to distribute air throughout the house. To ensure proper connections, minimize leaks and maximize efficiency, it is important to understand how to properly connect the duct work.
Connecting Round Ducts
Select duct pieces for the connection that have crimped and uncrimped ends. If one end is not crimped, you must crimp it by using the crimp tool, which looks like a pair of scissors. Place the sheet metal in between the two blades of the crimp tool, with the tool pointing into the duct. Squeeze, release and remove the crimp tool. Move the tool along the duct opening and repeat the squeeze-and-release procedure until you have created the crimped duct end.
Insert the crimped end of the round duct into the uncrimped end of the next round duct. If the ducts are difficult to attach, use one or two flat-head screwdrivers to guide one duct into the other.
Tape the seam of the duct connection with foil tape. Smooth the tape to prevent air leakage.
Insert a 1/2-inch-long self-tapping sheet-metal screw at the location where the two ducts overlap to provide a solid connection. Insert two additional screws along the seam, with equal spacing between the three screws. The three screws will prevent the two ducts from moving and separating at the new seam.
Connecting Rectangular Ducts
Attach S-cleats on two opposite raw metal edges of one duct to be attached. Make sure that the S-cleats are shorter than the length of the side being connected.
Align two rectangular ducts with the same dimensions.
Slip the two raw edges of the next duct into the S-cleats that were installed on the adjoining duct. If necessary, use a flat-head screwdriver to slightly open the S-cleat to provide easier installation. Continue pressing the two ducts together until the gap between the ducts is minimized.
Slip the drives onto the two remaining sides of the duct work, one at a time. Make sure that the drives are at least 2 inches longer than the side of the duct being attached. Leave 1 inch of drive hanging over each corner of the duct seam. Hammer the extra 1 inch of drive material over each corner of the duct seam to lock the drive in place and provide a greater airtight connection.
Tape the seam between the two ducts. Smooth the tape to ensure an airtight connection.
Elizabeth Sobiski has been writing professionally since 2005. She provides businesses such as Burdick and Lee Galleries, Clearwater Fishing Charters and Read Finder with custom content to keep their digital and print media fresh, informative and directed to their target audience. Sobiski holds a Bachelor of Arts in English from Roosevelt University in Chicago.