# How to Calculate Conduit Size for Wiring

Hunker may earn compensation through affiliate links in this story.

#### Tip

There are 22 pages of conduit fill tables published in chapter 9 of the NEC. Be sure you choose the correct table for the type of conduit and type of wire you will run through it.

#### Warning

Placing more than four wires in a conduit requires derating the ampacity of the wires to reduce the amount of current they are allowed to carry.

Electrical conduit has maximum fill rates for the number of wires it may carry.

National Electric Code (NEC) covers the use of conduit in its published codes and rules. Choosing the correct diameter conduit requires using NEC tables to find wire-type diameters, fill amounts and conduit diameters. NEC specifies that a single wire may use up to 53 percent of the space inside a conduit, two wires may only use up to 31 percent, and more than two wires may not exceed 40 percent of the total available space inside a conduit.

Video of the Day

## Step 1

Choose the fill table from NEC chapter 9 that matches the type of wire and conduit you are using. For example, table 14 is for EMT type conduit and THHN or THWN wire.

## Step 2

Determine the diameter of the conduit by the total amount of wires when placing the same gauge and type of wire inside a conduit. Read down the first column on the fill table to locate the wire gauge. Read across from the wire gauge to find the maximum number of wires you may place inside a given conduit diameter. Select a number equal to or greater than the number of wires you will place inside the conduit.

For example, to place 15, 12-gauge wires inside EMT conduit, read down the left-most column to find 12-gauge wire. Read across the 12-gauge row until you come to 16, which is the number of 12-gauge wires allowed in Â¾-inch EMT conduit.

## Step 3

Calculate the total diameter of the wires to determine the diameter of the conduit when placing wires of different gauge and type inside the conduit. Find the wire diameter in table 5 for each gauge wire and type. Multiply the number of wires for each gauge and type by the wire diameter. Total the results.

For example, to use six each of 12-gauge THHN wires and 14-gauge THHN wires, we find the wire diameter of each is 0.0133 and 0.0097 respectively.

6 x 0.0133 = 0.0798 and 6 x 0.0097 = 0.0582. Totaling the results: 0.0798 + 0.0582 = 0.138.