Most multimeters will have the setting for measuring AC power labeled in red, and those for measuring DC power in black. Using a digital multimeter can provide a quicker read out of the voltage being measured, and some newer models can auto-detect the voltage without having to manually select it on the multimeter.
If any of the voltages read below the values given in steps 3 and 4, consult a licensed electrician to check the circuit panel and wiring of the circuit. Avoiding letting your fingers touch any part of the metal tips on the test leads while they are inserted into the outlet as this could cause serious injury or electrocution. Follow the safety guidelines in the manual for your particular model multimeter.
Installing a new electric dryer may require testing the 220 volt outlet to ensure it is working and can provide the necessary voltage for proper and safe operation. Using a multimeter or sometimes called a VOM (Volt Ohm Meter), will provide an instant and accurate reading of the voltage in the outlet. The typical dryer requires 220 to 240 volts to run, and simply just plugging in the dryer to the outlet to see if it will work could cause damage to the dryer or electrical circuit if the voltage is not correct.
Video of the Day
Locate the circuit breaker for the 220 volt dryer outlet in the main circuit panel, which is typically located in the garage or utility room. The circuit breakers are labeled on the door of the panel, and the 220 volt circuit breaker will be a larger two pole breaker.
Turn the power on to the multimeter. Turn the selector knob to the AC side and select the closest know voltage setting to match that of what the outlet voltage should be. (i.e. A dryer outlet is typically 220 volts so you would select 220 to 240 VAC.)
Plug the two tester leads into the multimeter. Plug the red lead into the red, positive (+) jack, and the black lead into the black, negative (-) jack. The jacks are typically color coded so the user can easily identify and make the proper connections.
Insert the two test leads (one each) into the two "hot" slots of the outlet. For a three-prong outlet, the two "hot" slots will be slanted; for a four-prong outlet the two "hot" slots will be the two outside vertical slots. Once inserted, the voltage should read between 220 to 240 volts.
Insert the red test lead into one "hot" slot and the black test lead into the neutral slot. For both the three- and four-prong outlets, the neutral prong will be L-shaped. Once inserted the voltage should read between 110 to 120 volts. Move the red test lead to the other "hot" slot and the black lead in the neutral slot and again the voltage should read between 110 to 120 volts. Remove the test leads from the outlet, and turn the VOM to the "off" position.
Plug the dryer cord into the dryer outlet for operation.
Billy Brainard graduated with a Bachelor of Science degree in education from Trinity College. As the department chairman he was responsible for creating and writing the curriculum for 7-12 grade students. Currently he writes for eHow and works part time helping employees by creating and writing resumes to help in their job search.